A verification study of ultrasound transmission numerical simulation results with experiment results is presented in this paper. The work considers a model of a transformer tank which is filled with electro insulating oil. In the experiment, performed under laboratory conditions, an ultrasound wave is generated by a piezoelectric transducer that is fixed in the centre of the tank and measured by another transducer mounted inside the tank at three distances: 10, 20 and 30 cm from the sound source. The transducer is able to measure and generate acoustic waves in the ultrasound frequency band up to 1 MHz. The simulation considers numerical calculation of acoustic pressure distribution inside the tank in which acoustic source emits waves with frequency equal to 100 kHz. Verification analysis has confirmed consistency of the numerically calculated values with the measurement results.
The subject presented in this paper refers to measurements and assessment of the corrected sound pressure level values (noise) occurring around a medium-power transformer. The paper presents the values of noise accompanying the operation of the power object before and after its modernization, which consisted in repeated core pressing and replacement of the cooling system. The main aim of the research work was the assessment of the influence of the repair work on the noise level emitted into the environment.
On-load tap changers (OLTC) are some of the main transformer elements that make voltage adjustment in a power network possible. Their failures often cause shutdowns of distribution transformers. The paper presents research work aimed at the assessment of the technical condition of OLTCs by the acoustic emission method (EA). This method makes the OLTC diagnosis possible without the need of disconnecting the transformer from the system. The measurements were taken in laboratory conditions. The influence on the operation non-concurrence of the power tap changer contacts on the AE registered signals has been investigated. The signals registered were subjected to analyses in the time and time-frequency domains. The result analysis in the time domain was carried out using the Hilbert transform and calculating characteristic times for the particular runs. A short-time Fourier transform was used for the assessment of results in the time-frequency domain.
Topics of this article concern the study of the fundamental nature of the sonoluminescence phenomenon occurring in liquids. At the Institute of Electrical Power Engineering at Opole University of Technology the interest in that phenomenon known as secondary phenomenon of cavitation caused by ultrasound became the genesis of a research project concerning acoustic cavitation in mineral insulation oils in which a number of additional experiments performed in the laboratory aimed to determine the influence of a number of acoustic parameters on the process of the studied phenomenona. The main purpose of scientific research subject undertaken was to determine the relationship between the generation of partial discharges in high-voltage power transformer insulation systems, the issue of gas bubbles in transformer oils and the generated acoustic emission signals. It should be noted that currently in the standard approach, the phenomenon of generation of acoustic waves accompanying the occurrence of partial discharges is generally treated as a secondary phenomenon, but it can also be a source of many other related phenomena. Based on our review of the literature data on those referred subjects taken, it must be noted, that this problem has not been clearly resolved, and the description of the relationship between these phenomena is still an open question. This study doesn’t prove all in line with the objective of the study, but can be an inspiration for new research project in the future in this topic. Solution of this problem could be a step forward in the diagnostics of insulation systems for electrical Power devices based on non-invasive acoustic emission method.