The trigeneration systems for production of cold use sorption refrigeration machines: absorption and adsorption types. Absorption systems are characterized namely by better cooling coefficient of performance, while the adsorptive systems are characterized by the ability to operate at lower temperatures. The driving heat source temperature can be as low as 60-70 °C. Such temperature of the driving heat source allows to use them in district heating systems. The article focuses on the presentation of the research results on the adsorption devices designed to work in trigeneration systems.
This paper presents the possibility of reducing the demand for nonrenewable primary energy for buildings using a new conceptual adsorption system of cooling and heating supplied by solar energy. Moreover, the aim of this study is to shorten the payback time of investment in the standard adsorption cooling system through its integration with the heating system. Research has been carried out for an energy-efficient medium-sized single-family building with a floor area of 140 m2 and a heat load of 4.2 kW and cold load of 4.41 kW. It has been shown that the use of an adsorption system of cooling and heating supplied by solar energy decreased the demand for nonrenewable primary energy by about 66% compared to the standard building that meets the current requirements.
This paper is devoted to application of adsorption process for cooling power generation in a cooling devices. Construction and working principle of a water-silica gel adsorption chiller has been presented and the basic refrigeration cycle has been discussed. The article outlines behavior of a single-stage adsorption system influenced by changes in cycle time. The effect of cycle time and inlet chilled water temperatures on the main system performance parameters has been analysed