In the paper presented have been the results of the analysis of effectiveness of operation of binary power plant consisting of combined two Clausius-Rankine cycles, namely the binary cycle with water as a working fluid in the upper cycle and organic substance as a working fluid in the lower cycle, as well as a single fluid component power plant operating also in line with the C-R cycle for superheated steam, with water as a working fluid. The influence of the parameters of superheated steam in the upper cycle has been assessed as well as the type of working fluid in the lower cycle. The results of calculations have been referred to the single-cycle classical steam power plant operating at the same parameters of superheated steam and the same mass flow rate of water circulating in both cycles. On the basis of accomplished analysis it has been shown that the binary power plant shows a greater power with respect to the reference power plant.
This paper presents a method for assessing the degree of approaching the paper output of the Clausius-Rankine cycle to the Carnot cycle. The computations to illustrate its use were performed for parameters characteristic of the current state of development of condensing power plants as well as in accordance with predicted trends for their further enhancing. Moreover there are presented computations of energy dissipation in the machines and devices working in such a cycle.
The paper is devoted to the problems of exergetic cost determination. A brief description of theoretical fundamentals of exergetic cost determination and its application are presented. The applied method of calculations is based on the rules of determination of cumulative exergy consumption. The additional possibilities ensured by the exergetic cost analysis in comparison to the direct exergy consumption analysis are discussed. The presented methodology was applied for the analysis of influence of operational parameters on exergetic cost indices of steam power plant. Results of calculations concern one of the modern Polish power plant unit. Basing on the obtained results several conclusions have been formulated that show advantages of application of exergetic cost analyses.
The article analyses selected aspects of the technology and logistics used to modernise a coal-fired heating plant to switch to woodchips, which is illustrated with a specific investment. The study presents characteristics of the investment’s heat economy before the modernisation, as well as the assumptions and program of the project. Finally, selected effects of the modernisation have been described
Secure and cost-effective power generation has become very important nowdays. Care must be taken while designing and operating modern steam power plants. There are regulations such as German boiler regulations (Technische Regeln für Dampfkessel 301) or European Standards that guide the user how to operate the steam power plants. However, those regulations are based on the quasi-steady state assumption and one dimensional temperature distribution in the entire element. This simplifications may not guarantee that the heating and cooling operations are conducted in the most efficient way. Thus, it was important to find an improved method that can allow to establish optimum parameters for heating and cooling operations. The optimum parameters should guarantee that the maximum total stresses in the construction element are in the allowable limits and the entire process is conducted in the shortest time. This paper summarizes mathematical descriptions how to optimize shut down process of power block devices. The optimization formulation is based on the assumption that the maximum total stresses in the whole construction element should be kept within allowable limits during cooling operation. Additionally, the operation should be processed in the shortest time possible.
High-temperature solid oxide fuel cells (SOFCs) are considered as suitable components of future large-scale clean and efficient power generation systems. However, at its current stage of development some technical barriers exists which limit SOFC’s potential for rapid large-scale deployment. The present article aims at providing solutions to key technical barriers in SOFC technology. The focus is on the solutions addressing thermal resistance, fuel reforming, energy conversion efficiency, materials, design, and fuel utilisation issues.
The paper presents a literature review on the topic of vapour power plants working according to the two-phase thermodynamic cycle with supercritical parameters. The main attention was focused on a review of articles and papers on the vapour power plants working using organic circulation fluids powered with low- and medium-temperature heat sources. Power plants with water-steam cycle supplied with a high-temperature sources have also been shown, however, it has been done mainly to show fundamental differences in the efficiency of the power plant and applications of organic and water-steam cycles. Based on a review of available literature references a comparative analysis of the parameters generated by power plants was conducted, depending on the working fluid used, the type and parameters of the heat source, with particular attention to the needs of power plant internal load.
The paper presents a thermodynamic optimization of supercritical coal fired power plant. The aim of the study was to optimize part of the thermal cycle consisted of high-pressure turbine and two chosen highpressure feed water heaters. Calculations were carried out using IPSEpro software combined with MATLAB, where thermal efficiency and gross power generation efficiency were chosen as objective functions. It was shown that the optimization with newly developed framework is sufficiently precise and its main advantage is the reduction of computation time on comparison to the classical method. The calculations have shown the tendency of the increase in efficiency, with the rise of a number of function variables.
This article describes the validation of a supercritical steam cycle. The cycle model was created with the commercial program GateCycle and validated using in-house code of the Institute of Power Engineering and Turbomachinery. The Institute's in-house code has been used extensively for industrial power plants calculations with good results. In the first step of the validation process, assumptions were made about the live steam temperature and pressure, net power, characteristic quantities for high- and low-pressure regenerative heat exchangers and pressure losses in heat exchangers. These assumptions were then used to develop a steam cycle model in Gate-Cycle and a model based on the code developed in-house at the Institute of Power Engineering and Turbomachinery. Properties, such as thermodynamic parameters at characteristic points of the steam cycle, net power values and efficiencies, heat provided to the steam cycle and heat taken from the steam cycle, were compared. The last step of the analysis was calculation of relative errors of compared values. The method used for relative error calculations is presented in the paper. The assigned relative errors are very slight, generally not exceeding 0.1%. Based on our analysis, it can be concluded that using the GateCycle software for calculations of supercritical power plants is possible.
Proposed is the analysis of steam condensation in the presence of inert gases in a power plant condenser. The presence of inert, noncondensable gases in a condenser is highly undesirable due to its negative effect on the efficiency of the entire cycle. In general, thermodynamics has not provided an explicit criterion for assessing the irreversible heat transfer process. The method presented here enables to evaluate precisely processes occurring in power plant condensers. This real process is of particular interest as it involves a number of thermal layers through which heat transfer is observed. The analysis was performed using a simple, known in the literature and well verified Berman’s model of steam condensation in the presence of non-condensable gases. Adapted to the geometry of the condenser, the model enables, for instance, to recognise places where non-condensable gases are concentrated. By describing with sufficient precision thermodynamic processes taking place in the vicinity of the heat transfer area segment, it is possible to determine the distributions of thermodynamic parameters on the boundaries between successive layers. The obtained results allow for the recognition of processes which contribute in varying degrees to irreversible energy degradation during steam condensation in various parts of the examined device.
The paper covers problems of the owners of a fleet of long-operated conventional power plants that are going to be decommissioned soon in result of failing to achieve new admissible emissions levels or exceeding pressure elements design lifetime. Energoprojekt-Katowice SA, Siemens AG and Rafako SA presents their joint concept of the solution which is a 2on1 concept – replacing two unit by two ultra-supercritical boilers feeding one turbine. Polish market has been taken as an example.
The present work is devoted to the problem of utilization of the waste heat contained in the exhaust gases having the temperature of 350 °C. Conversion of the waste heat into electricity using a power plant working with organic fluid cycles is considered. Three Organic Rankine Cycle (ORC) power plant solutions are analysed and compared: a solution with the basic, single thermodynamic conversion cycle, one with internal heat recuperation and one with external heat recuperation. It results from the analysis that it is the proper choice of the working fluid evaporation temperature that fundamentally affects the maximum of the ORC plant output power. Application of the internal heat recuperation in the plant basic cycle results in the output power increase of approx. 5%. Addition of the external heat recuperation to the plant basic cycle, in the form of a secondary supercritical ORC power cycle can rise the output power by approx. 2%.
The internal diameter of a tube in a ‘church window’ condenser was estimated using an entropy generation minimization approach. The adopted model took into account the entropy generation due to heat transfer and flow resistance from the cooling-water side. Calculations were performed considering two equations for the flow resistance coefficient for four different roughness values of a condenser tube. Following the analysis, the internal diameter of the tube was obtained in the range of 17.5 mm to 20 mm (the current internal diameter of the condenser tube is 22 mm). The calculated diameter depends on and is positively related to the roughness assumed in the model.
In order to analyze the cumulative exergy consumption of an integrated oxy-fuel combustion power plant the method of balance equations was applied based on the principle that the cumulative exergy consumption charging the products of this process equals the sum of cumulative exergy consumption charging the substrates. The set of balance equations of the cumulative exergy consumption bases on the ‘input-output method’ of the direct energy consumption. In the structure of the balance we distinguished main products (e.g. electricity), by-products (e.g. nitrogen) and external supplies (fuels). In the balance model of cumulative exergy consumption it has been assumed that the cumulative exergy consumption charging the supplies from outside is a quantity known a priori resulting from the analysis of cumulative exergy consumption concerning the economy of the whole country. The byproducts are charged by the cumulative exergy consumption resulting from the principle of a replaced process. The cumulative exergy consumption of the main products is the final quantity.
The objective of the paper is to analyse thermodynamical and operational parameters of the supercritical power plant with reference conditions as well as following the introduction of the hybrid system incorporating ORC. In ORC the upper heat source is a stream of hot water from the system of heat recovery having temperature of 90 °C, which is additionally aided by heat from the bleeds of the steam turbine. Thermodynamical analysis of the supercritical plant with and without incorporation of ORC was accomplished using computational flow mechanics numerical codes. Investigated were six working fluids such as propane, isobutane, pentane, ethanol, R236ea and R245fa. In the course of calculations determined were primarily the increase of the unit power and efficiency for the reference case and that with the ORC.
In the paper presented is an idea of organic Rankine cycle (ORC) operating with supercritical parameters and so called dry fluids. Discussed is one of the methods of improving the effectiveness of operation of supercritical cycle by application of internal regeneration of heat through the use of additional heat exchanger. The main objective of internal regenerator is to recover heat from the vapour leaving the turbine and its transfer to the liquid phase of working fluid after the circulation pump. In effect of application of the regenerative heat exchanger it is possible to obtain improved effectiveness of operation of the power plant, however, only in the case when the ORC plant is supplied from the so called sealed heat source. In the present paper presented is the discussion of heat sources and on the base of the case study of two heat sources, namely the rate of heat of thermal oil from the boiler and the rate of heat of hot air from the cooler of the clinkier from the cement production line having the same initial temperature of 260 oC, presented is the influence of the heat source on the justification of application of internal regeneration. In the paper presented are the calculations for the supercritical ORC power plant with R365mfc as a working fluid, accomplished has been exergy changes and exergy efficiency analysis with the view to select the most appropriate parameters of operation of the power plant for given parameters of the heat source.
The paper presents an analysis of the sustainable development of electricity generation sources in the National Power System (NPS). The criteria to be met by sustainable power systems were determined. The paper delineates the power balance of centrally dispatched power generation units (CDPGU), which is required for the secure work of the NPS until 2035. 19 prospective electricity generation technologies were defined. They were divided into the following three groups: system power plants, large and medium combined heat and power (CHP) plants, as well as small power plants and CHP plants (distributed sources). The quantities to characterize the energy effectiveness and CO2 emission of the energy generation technologies analyzed were determined. The unit electricity generation costs, discounted for 2018, including the costs of CO2 emission allowance, were determined for the particular technologies. The roadmap of the sustainable development of the generation sources in the NPS between 2020 and 2035 was proposed. The results of the calculations and analyses were presented in tables and figure
The aim of this paper is to analyze various CO2 compression processes for post-combustion CO2 capture applications for 900 MW pulverized coal-fired power plant. Different thermodynamically feasible CO2 compression systems will be identified and their energy consumption quantified. A detailed thermodynamic analysis examines methods used to minimize the power penalty to the producer through integrated, low-power compression concepts. The goal of the present research is to reduce this penalty through an analysis of different compression concepts, and a possibility of capturing the heat of compression and converting it to useful energy for use elsewhere in the plant.
The large variability and unpredictability of energy production from photovoltaic power microinstallations results from the dependence on the current weather conditions. These conditions depend on a number of factors and are variable over the time. Despite this specificity, photovoltaic micro-installations are becoming more and more popular in the world and in Poland. This is mainly due to the fact that the generation of energy from renewable sources has numerous advantages, the energy is free, renewable in time and ecological, and its production on its own gives partial independence from energy supplies from the power grid. In addition, the observed significant prices decrease of solar modules has further accelerated the development of the use of this energy source. Concern for this method of energy production among households has increased significantly in Poland after introducing the prosumer in the legal framework and the use of administrative and financial support. The implemented prosumer mechanisms allowed, for example, the net balancing of the energy consumed and produced by the micro-installation through storage in the power grid. The article describes the problem of balancing sources using solar energy, based on micro-installation used in the household (the so-called prosumer installation). The conducted analyses compared the load profile of a typical household and the energy generation profile from a photovoltaic installation, determining the real balancing formation level of such a system.
The paper discusses the feasibility, effectiveness and validity of a gas turbine power plant, operated according to the Brayton comparative cycle in order to develop low-potential waste heat (160◦C) and convert it into electricity. Fourteen working fluids, mainly with organic origin have been examined. It can be concluded that low molecular weight working fluids allow to obtain higher power efficiency of Brayton cycle only if conversions without taking into account internal losses are considered. For the cycle that takes into account the compression conversion efficiency in the compressor and expansion in the gas turbine, the highest efficiency was obtained for the perfluoropentane working medium and other substances with relatively high molecular weight values. However, even for the cycle using internal heat recovery, the thermal efficiency of the Brayton cycle did not exceed 7%.The paper discusses the feasibility, effectiveness and validity of a gas turbine power plant, operated according to the Brayton comparative cycle in order to develop low-potential waste heat (160◦C) and convert it into electricity. Fourteen working fluids, mainly with organic origin have been examined. It can be concluded that low molecular weight working fluids allow to obtain higher power efficiency of Brayton cycle only if conversions without taking into account internal losses are considered. For the cycle that takes into account the compression conversion efficiency in the compressor and expansion in the gas turbine, the highest efficiency was obtained for the perfluoropentane working medium and other substances with relatively high molecular weight values. However, even for the cycle using internal heat recovery, the thermal efficiency of the Brayton cycle did not exceed 7%.
In this paper an air separation unit was analyzed. The unit consisted of: an ionic transport membrane contained in a four-end type module, an air compressor, an expander fed by gas that remains after oxygen separation and heat exchangers which heat the air and recirculated flue gas to the membrane operating temperature (850 °C). The air separation unit works in a power plant with electrical power equal to 600 MW. This power plant additionally consists of: an oxy-type pulverized-fuel boiler, a steam turbine unit and a carbon dioxide capture unit. Life steam parameters are 30 MPa/650 °C and reheated steam parameters are 6 MPa/670 °C. The listed units were analyzed. For constant electrical power of the power plant technical parameters of the air separation unit for two oxygen recovery rate (65% and 95%) were determined. One of such parameters is ionic membrane surface area. In this paper the formulated equation is presented. The remaining technical parameters of the air separation unit are, among others: heat exchange surface area, power of the air compressor, power of the expander and auxiliary power. Using the listed quantities, the economic parameters, such as costs of air separation unit and of individual components were determined. These quantities allowed to determine investment costs of construction of the air separation unit. In addition, they were compared with investment costs for the entire oxy-type power plant.
This article describes a thermodynamic analysis of an oxy type power plant. The analyzed power plant consists of: 1) steam turbine for supercritical steam parameters of 600 °C/29 MPa with a capacity of 600 MW; 2) circulating fluidized bed boiler, in which brown coal with high moisture content (42.5%) is burned in the atmosphere enriched in oxygen; 3) air separation unit (ASU); 4) CO2 capture installation, where flue gases obtained in the combustion process are compressed to the pressure of 150 MPa. The circulated fluidized bed (CFB) boiler is integrated with a fuel dryer and a cryogenic air separation unit. Waste nitrogen from ASU is heated in the boiler, and then is used as a coal drying medium. In this study, the thermal efficiency of the boiler, steam cycle thermal efficiency and power demand were determined. These quantities made possible to determine the net efficiency of the test power plant.
The paper presents a thermodynamic optimization of 900MW power unit for ultra-supercritical parameters, modified according to AD700 concept. The aim of the study was to verify two optimisation methods, i.e., the finding the minimum of a constrained nonlinear multivariable function (fmincon) and the Nelder-Mead method with their own constrain functions. The analysis was carried out using IPSEpro software combined with MATLAB, where gross power generation efficiency was chosen as the objective function. In comparison with the Nelder-Mead method it was shown that using fmincon function gives reasonable results and a significant reduction of computational time. Unfortunately, with the increased number of decision parameters, the benefit measured by the increase in efficiency is becoming smaller. An important drawback of fmincon method is also a lack of repeatability by using different starting points. The obtained results led to the conclusion, that the Nelder-Mead method is a better tool for optimisation of thermal cycles with a high degree of complexity like the coal-fired power unit.
The small number of available complete modern pump characteristics makes the safety analysis of nuclear and conventional power plants based on the characteristics made over half a century ago of specific speeds n_q=24.6, 147.1 and 261.4. The aim of the paper is to check sensitivity of the power plant system response for different complete pump characteristics - modern and available from older tests for n_q=24.6, 147.1 and 261.4. It has been shown that Suter's characteristics for modern pumps give a different response to the pumping system of a power plant in breakdown than those used so far.
Using renewable energy sources for electricity production is based on the processing of primary energy occurring in the form of sun, wind etc., into electrical energy. Economic viability using those sources in small power plants strongly depends on the support system, based mainly on financial instruments. Micro-installations, by using special instruments dedicated to the prosumer market may become more and more interesting not only in terms of environmental energy, but also financial independence. In the paper, the term hybrid power plant is understood to mean a production unit generating electricity or electricity and heat in the process of energy production, in which two or more renewable energy sources or energy sources other than renewable sources are used. The combination of the two energy sources is to their mutual complementarity, to ensure the continuity of the electricity supply. The ideal situation would be if both sources of energy included in the hybrid power plant continuously covered the total demand for energy consumers. Unfortunately, due to the short-term and long-term variability of weather conditions, such a balance is unattainable. The paper assesses the possibility of balancing the hybrid power plant in daily and monthly periods. Basic types of power plants and hybrid components and system support micro-installations were characterized. The support system is based particularly on a system of feed-in tariffs and the possibility of obtaining a preferential loan with a subsidy (redemption of part of the loan size). Then, an analysis of energy and economic efficiency for a standard set of hybrid micro-installations consisting of a wind turbine and photovoltaic panels with a total power of 5 kW, were presented. Fourteen variants of financing, economic efficiency compared with the use of the method of the simple payback period were assumed.